Welcome to our Picture Area of HVAC equipment in NJ we work on. Some of the
pictures have a caption that might help you diagnose your HVAC system. These
pictures are of industrial/commercial HVAC equipment in NJ. Most of the
equipment brands are
Air Coil), AAon® and general HVAC systems.
*These pictures are for your viewing. If you wish to use our pictures,
please save a copy of them and upload these pictures to your own hosting
This Aerco boiler is a high efficiency boiler. It Is used in
this application for heating domestic water.
It's amazing how small it is and is 1 million BTU's
Here we have the case off, giving it a yearly maintenance.
Changing igniter and flame sensor. Also reaming all the carbon
build up inside the tubes.
Bearing went bad and worn down shaft
The next pictures are of a AAon unit in NJ. The condenser motor fan
brackets broke which sent this motor into the condenser coil. The
fan blade cut about 30+ holes into the coil. We were able to fix 5
of the 6 coil sections in this unit. Unfortunately one of the coils
had to be replaced due to too many holes.
Broken bracket on second condenser fan motor in
Re-welding 2 new condenser fan motor brackets back
in we got from AAon®.
This picture is a HB Smith boiler in Northern NJ. The fire box
was in dire need of repair.
Here's a little view of the inside of the boiler before we
repaired the fire box before start up.
A picture of a new installation of Data Aire® dry coolers in
Jersey City NJ. 180 fans!
A small BAC® cooling tower getting a cleaning
A few larger BAC® water towers
Ray Pak Boilers - These are high efficiency
modulating commercial boilers.
6 inch clogged valve. This was clogged with soot from dirty water tower water.
Changing filters inside this Mammoth® Unit and more pictures of
this same unit.
Data Aire® unit that froze up after because of free cooling valve
and 2 stages of cooling on at the same time.